In accordance with AS/NZS 1596:2014: The storage and handling of LP Gas, electrical connections should have a minimum 1.5 metre exclusion zone from gas cylinders (figure 1). Ignition sources are to be kept clear of this exclusion zone. Ignitions sources include, but are not limited to, electrical appliances or equipment, switchboards, switches, junction boxes, Telstra Network Termination Devices...
Building and Energy
19 Aug 2019