Dunsborough bushfire - 7 February 2009
All documents issued prior to 1 July 2017 were issued by the former Department of Commerce. Documents listed here are the latest versions available, but may be subject to review. For more information on this document, please contact firstname.lastname@example.org.
EnergySafety carried out an investigation into the cause of the fire in Dunsborough. It was determined that the cause of the fire was a leakage current due to dust or salt spray on the insulators, combined with light rain and high humidity. The current generated enough heat to ignite the wood and the falling hot embers ignited the vegetation on the ground.
Share this page: