Yallingup bushfire - 5 January 2015
All documents issued prior to 1 July 2017 were issued by the former Department of Commerce. Documents listed here are the latest versions available, but may be subject to review. For more information on this document, please contact email@example.com.
EnergySafety carried out an investigation into the bushfire at Yallingup and found that a 22kV Cable Head Termination on a Western Power concrete pole failed as a result of the cable’s paper insulation failure. This failure resulted in a short circuit and explosion causing hot molten metal fragments to ignite the dry grass at the base of the pole which started the bushfire.
Share this page: